Original Well Production – 1,200 GPM
Before Redi Clean Treatment – 150 GPM
After Redi Clean Treatment – 1,000 GPM
We have treated several wells with Redi Clean chemicals with great success. The technical assistance involved with the treatments very definitely helps us understand how we need to rehabilitate wells to get the desired end results.
Our clients have been consistently happier with the end results since we have been using Redi Clean to rehabilitate our wells.
I would and do recommend Redi Clean to clients and friends for their chemicals and treating recommendations. It is refreshing to use someone’s product who actually has the field experience to recommend modifications when you run in to unique situations.
Our most recent well we rehabilitated had previously been relined. Before it was relined it produced 1,200 gallons per minute. After it was relined it was never better than 800 GPM. Over the years the production had dropped down to 150 GPM.
The treatment recommendations suggested jetting off the hard, heavy iron bacteria. From there, we were to surge block, clean the bottom and do a final round of surge blocking with Redi Clean Acid™. The pump was installed and is now making a consistent 1,000 gallons per minute.
The results speak for themselves.
Emil Worm, L.O. Lynch
856 W. Seventh Street
San Jacinto, California 92582
(888) 654-7724 | lynchwells.com
Original Well Production – 1,200 GPM
Previous Treatments – brought well to 800 GPM and would decrease back to 400 GPM after 6 weeks
Before Redi Clean Treatment – 400 GPM
After Redi Clean Treatment – 1,200 GPM
Don Teeters and I met at a ground water presentation where Don was speaking on well rehabilitation. This subject was a bit of a touchy one, as I was frustrated with the acid product I was currently using and the lack of support that that chemical company had offered me. Whenever I called that company for help to ask why my well efficiencies were not improving I always got the same answer. Use more product.
As I listened to Don, he was answering my question about a reliable product as well as technical support. I decided to give him a shot. I used Redi Clean products on 2 wells just by filling out a questionnaire online. Don was there for any questions I had, and he explained the reasoning behind his recommendations, educating me to not make the same old mistakes. I got the results that I needed.
When talking to Don, I mentioned I had turned down a city well that was 1,200 GPM that was currently down to 400 GPM. It was acidized yearly and would increase to 800 GPM and after 6 weeks drop back down to 400 GPM again. Don encouraged me to accept that job and was confident I would be able to bring the well back to 1,200 GPM. So with the reliable Redi Clean chemical line and Don’s consulting, the well recovered back to 1,200 GPM.
I believe that Redi Clean not only has a superior product, but they genuinely care about the success of their treatments. Don Teeters, who is the president of the company, is always available to take calls and help. I have even had him show up on jobsites to make sure things go well!
I have used Redi Clean products for 10 years, including their technical support. My business and reputation has improved every year because of the reliability of their product and service. I tried a lot of products previous to Redi Clean, but it is my belief that Redi Clean is over and above anything else out on the market.
Terry Alexander, Alexander Pump Service, Inc.
Saint Mary’s, Kansas
(785) 437-2394 | alexanderpump.com
Original Well Production – 230 GPM @ 400’ of THD
Before Redi Clean Treatment – 80 GPM
After Redi Clean Treatment – 243 GPM @ 349’ of THD
This well is unique in the fact that it is only 9 years old. From the date of construction this well produced heavy amounts of sand. Therefore the engineer on record redesigned the well and installed an 8” inner casing, see the drawing for reference.
This well has lost production steadily for several years. During the first week of May 2012 this well drew down to the point of surging. Prior to the extreme drawdown the well was producing 80GPM. Designed production was 230 GPM.
Well video was taken along with a water sample and residue sample that were sent off to SDK lab and Redi Clean. The results of the tests showed heavy Iron Bacteria fouling of the gravel pack and perforations.
Valley Pump performed a complete well restoration using Redi Clean chemicals as directed by Don Teeters via a written recommendation detailing the complete procedure.
After completing the restoration a new pump bowl was installed. The bowl was designed for 230 GPM @ 400’ of THD. After the pump plant station went back on line it is now producing 243 GPM @ 349’ TDH.
Woody Miller, Valley Pump & Dairy Systems
10475 14th Street
Armona, CA 93202
(559) 587-1000 | vpdsinc.com